- The media list in the technical description must be observed.
- The leak protection lining in single-walled tanks must have a general building approval (certificate earlier).
- The max. viscosity allowed for the corresponding application must be observed. - For example DIN EN 12285: max. 5 × 10-3 m2/s.
- Installation of a potential free relay.
- Installation in protective casing, with external heating and alarm.
- Mounting Kits (MBS) for the corresponding container ports.
Please click on the picture for a larger view!